Centurion - Combination of Eyewash and Safety Shower
Shower is activated by pull rod and eye wash is activated by flag handle or foot treadle. Two spray type outlet heads deliver a flood of water for rinsing eyes.
Shower Head: 10" diameter head provide water flow.
Shower Valve: 1" IPS chrome plated brass valve, Valve is acivated by pull rod.
Spray Head Assembly: Two spray heads. Each head has a dust cover, Internal flow control and filter to remove impurities from the water flow.
Eye Wash Bowl: 11-1/2" diameter. Bowl is ABS plastic.
Eye wash Valve: 3/8' IPS chrome plated brass stay-open ball valve. Valve is activated by flag handle or fool treadle. Unit remains in operation until handle is returned to closed position.
Pipe and Fittings: Schedule 1" and 1/2 galvanized steel, furnished with green polyethylene covers for vertical piping for corrosion resistance.
Supply: 1-1/4" NPT female inlet
Waste : 1-1/4" NPT female outlet.
Quality Assurance:Valve, Bowl and spray head assembly is factory assembled.
Outlets heads position meets: ANSI Z358.1-2014, EN 15154-1:2006 & EN 15154-2:2006, AS 4775:2007